# RELAI ARUS LEBIH OVERCURRENT RELAY.

## Presentasi berjudul: "RELAI ARUS LEBIH OVERCURRENT RELAY."— Transcript presentasi:

RELAI ARUS LEBIH OVERCURRENT RELAY

FUNGSI APLIKASI SEBAGAI PENGAMAN UTAMA ATAU CADANGAN
UNTUK GANGGUAN HUBUNG SINGKAT FASA – FASA FASA – TANAH APLIKASI PENGAMAN UTAMA JTM ( DISTRIBUSI ) GENERATOR ( Kapasitas kecil ) TRAFO DAYA ( Kapasitas kecil ) MOTOR MOTOR BESAR SEBAGAI PENGAMAN CADANGAN

RELAI ARUS LEBIH SUATU RELAI YANG BEKERJANYA
PENGERTIAN RELAI ARUS LEBIH SUATU RELAI YANG BEKERJANYA BERDASARKAN ADANYA KENAIKAN ARUS YANG MELAMPAUI NILAI SETTINGNYA .

JENIS RELAI ARUS LEBIH NON DIRECTIONAL DIRECTIONAL KONTROL TEGANGAN
PENAHAN TEGANGAN

1. TIDAK BERARAH ( NON DIRECTIONAL )
KARAKTERISTIK @ ARAH 1. TIDAK BERARAH ( NON DIRECTIONAL ) 2. BERARAH ( DIRECTIONAL ) @ ARUS – WAKTU 1. TANPA TUNDA ( MOMENT = INSTANT ) 2. TUNDA WAKTU ( TIME DELAY ) # DEFINITE ( TERTENTU ) = INDEPENDEN # INVERSE ( I – t BERBANDING TERBALIK ) = DEPENDEN SI / NI = Standard / Normal Iverse VI = Very Inverse EI = Exteremely Inverse LTI = Long Time Invers

KARAKTERISTIK INSTANT = MOMENT

KARAKTERISTIK TUNDA WAKTU TERTENTU ( DEFINITE TIME )

KARAKTERISTIK TUNDA WAKTU INVERSE
KURVA (TMS / Td )

KARAKTERISTIK KOMBINASI INSTANT DENGAN TUNDA WAKTU TERTENTU (DEFINITE TIME )

KARAKTERISTIK KOMBINASI INSTANT DENGAN TUNDA WAKTU INVERSE

TIPE PLUNGER Fp Fe Fe = GAYA ELEKTROMEKANIK Fp = GAYA PEGAS KONTAK
0.6 BELITAN 0.8 Fe 1.0 1.2 INTI LUAR SETTING Faktor Pabrik Fe = GAYA ELEKTROMEKANIK Fp = GAYA PEGAS Fe < Fp DROP OFF Fe > Fp PICK UP

Mempunyai karakteristik Inverse
TIPE KWH KUMPARAN LAGGING PIRINGAN Is KUMPARAN UTAMA I Mempunyai karakteristik Inverse

SETTING ARUS DAN WAKTU TAP / PLUG SETING TIME DIAL SETTING TAP SETTING
KUMPARAN UTAMA ARUS DARI CT KONTAK DIAM DENGAN MENGATUR JARAK KONTAK TIME DIAL SETTING KONTAK GERAK

TIPE RELAI STATIK A CT RECTIFIER I R SETTING SUPLAI DC LEVEL DETECTOR
BANTU

BLOK DIAGRAM RELAI ARUS LEBIH STATIK
CURVE SHAPER FILTER CS R F Ia F Is MAX I GATE & RECT. RL Ib LD 1 LD 2 T 1 Ic Is INSTANT RL LD 3 3 LD = LEVEL DETECTOR T = TIMER R = REGULATOR SETTING INSTANT IBA DOC

STATIC OVER CURRENT RELAY
HS OUTPUT RELAY STATIC OVER CURRENT RELAY MCGG OUTPUT DRIVER TIME / CURRENT OUTPUT RELAY HS TIME 0.4/0 FULLWAVE RECTIFIER MICRO COMPUTER 0.2/0 INTERPOSSING CT 0.2/0 0.1/0 0.05/0 INPUT 0.05/0.025 TMS SWITH SETTING A/D 16/0 8//0 0.2/0.1 0.4/0 0.8/0 4//0 0.2/0 0.4/0 2/0 1/0 CURRENT SETTING HIGH SET SWITH SETTING CURVE SELECT SWITCH IBA DOC

RELAI OCR / GFR TIPE MCGG 82
B C E INST t I > Is NAME PLATE RESET KARAK TERISTIK RELAI OCR / GFR TIPE MCGG 82 IBA DOC

* Is = k In In = Arus Nominal k = Faktor pabrik ( 1 s/d 2 )
PRINSIP/CARA SETTING OCR # Iset Tunda waktu ( I > /Io>) * Is = k In In = Arus Nominal k = Faktor pabrik ( 1 s/d 2 ) atau 0,05 s/d 2,4 dengan step 0.05 * Plug Setting * Numeric IBA DOC

# Waktu kerja (t> / to> )
* Definite ( Langsung atau dengan Tms ) * Inverse ( Td atau Tms dan Mps = I / Is ) t Td = Time dial setting Tms = Time multiple seting Mps = Multiple plug setting …. X Is tk tk Tms ( td ) 1,0 0,6 x Is Mps = 4 x Is IBA DOC

# Is instant /moment ( I>> / Io>> )
* Is instant = k In atau k Is In = Arus Nominal Is = Arus setting tunda waktu k = Faktor pabrik * Plug setting * Numeric IBA DOC

DENGAN MENGGUNAKAN OCR / GFR TIPE MCGG82
CONTOH CARA SETTING DENGAN MENGGUNAKAN OCR / GFR TIPE MCGG82 @ SETTING ARUS OCR /GFR DENGAN TUNDA WAKTU 0.1 0.05 0.1 0.2 ARUS SETTING 0.4 0.4 ARUS NOMINAL RELAI 0.4 0.8 FAKTOR PABRIK IBA DOC

Is = 1.2 In Is = ( 0.1 + 0.1 + 0.2 + 0 + 0 + 0 + 0.8 ) x 5A = 1,2 x 5A
# MISAL ARUS SETTING Is = 6 A. Is = 1.2 In POSISI SAKLAR : 0.1 0.05 0.1 0.2 Is = ( ) x 5A = 1,2 x 5A = 6 A 0.4 0.4 0.4 0.8 IBA DOC

SI VI EI LTI D2 D4 D8 1 PEMILIHAN KARAKTERISTIK 1 1 1 1 1 1
1 TRIP TEST : CURVA SI : 1 1 1 1 1 1 IBA DOC

KURVA / KARAKTERISTIK @ STANDARD / NORMAL INVERSE ( SI )
@ VERY INVERSE ( VI ) @ EXTREMELY INVERSE ( EI ) @ LONG TIME INVERSE ( LTI ) IBA DOC

MISAL : KARAKTERISTIK EI
SETTING WAKTU MISAL : KARAKTERISTIK EI ARUS GANGGUAN 3 x Is ( I = 3 ) WAKTU KERJA = 1 DETIK PEMILIHAN TMS : POSISI SAKLAR 0,025 0,05 0,05 0,1 0,2 0,2 0,4 IBA DOC

SETTING INSTANT POSISI SAKLAR 1 2 4 8 16 IBA DOC

I> = 5A; Io> = 1A ; I>> = 35A
20KV X DATA SETTING I> = 5A; Io> = 1A ; I>> = 35A t>=0,5 detik ;to>=0,5 detik Karakteristik tunda waktu = SI P1 50 / 51 51N 300/5A 10P15 30VA P2 In relai = 5A Io>> tdk aktip F Ihs3f=3300A Ihs2f=2000A Ihs!f= 210A

- + Is Is Is Is MCGG 82 INDICATOR RESET TMS SETTING INST SETTING CURVE
SELECTION 49 50 < < TIME DELAY TRIP 21 < < 13 POWER SUPPLY CIRCUIT + Is INST TRIP 14 - Vx 22 INPUT CIRCUIT Ph CURRENT SETTING Ph < < RL 1-1 35 33 34 PHASE FAULT TIME DELAYED TRIP OUTPUT CONTACT TMS SETTING INST SETTING CURVE SELECTION 47 RL 1-2 29 48 TIME DELAY TRIP < 30 23 < < < OUTPUT CIRCUIT Ph INST TRIP Is RL 2-1 36 24 37 CURRENT SETTING Ph < < PHASE FAULT INSTATANEOUS TRIP OUTPUT CONTACT INPUT CIRCUIT Ph 38 RL 2-2 41 42 TMS SETTING INST SETTING CURVE SELECTION 45 46 RL 3-1 TIME DELAY TRIP 7 < < 6 25 EARTH FAULT TIME DELAYED TRIP OUTPUT CONTACT < < 5 Is INST TRIP RL 3-2 2 26 INPUT CIRCUIT Ph CURRENT SETTING Ph < < 1 OUTPUT CIRCUIT E/F RL 4-1 8 43 TMS SETTING INST SETTING CURVE SELECTION 10 9 EARTH FAULT INSTATANEOUS TRIP OUTPUT CONTACT 44 TIME DELAY TRIP RL 4-2 16 < < 27 < < 15 Is INST TRIP 28 INPUT CIRCUIT E/F CURRENT SETTING E/F < <

Sambungan tipe 3 OCR + 1 GFR
SAMBUNGAN ( WIRING ) Sambungan tipe 3 OCR + 1 GFR OCR PMT OCR GFR R P1 S E T S1 CT OCR S2 P2 Diagram AC IBA DOC

Sambungan tipe 2 OCR + 1 GFR
PMT OCR GFR R P1 E T S1 CT OCR S2 P2 Diagram AC IBA DOC

PENGUJIAN RELAI ARUS LEBIH
PENGUJIAN INDIVIDUAL MENGUJI INDIVIDU RELAI ITU SENDIRI , UNTUK MENGETAHUI APAKAH MASIH DALAM KEADAAN STANDAR ATAU TIDAK PENGUJIAN FUNGSI MENGUJI FUNGSI DARI SISTEM PROTEKSI SECARAKESELURUHANAPAKAH MASIH BERFUNGSI ATAU TIDAK

PENGUJIAN INDIVIDUAL HAL HAL YANG PERLU DIPERHATIKAN : CARA SETTING
INTERNAL DIAGRAM RELAI ALAT UJI / RANGKAIAN PENGUJIAN ITEM PENGUJIAN PROSEDUR PENGUJIAN HASIL UJI DAN KESIMPULAN

JENIS / ITEM PENGUJIN ARUS PICK UP DAN ARUS DROP OFF SERTA
RASIO ARUS PICK UP DENGAN DROP OFF KARAKTERISTIK ARUS – WAKTU KARAKTERISTIK INSTANTANEOUS

ARUS PICK UP [ ARUS AWAL / MULA ]
ARUS MINIMUM YANG MENYEBABKAN RELAI BEKERJA ARUS DROP OFF [RESET/ KEMBALI ] ARUS MAKSIMUM YANG MENYEBABKAN RELAI TIDAK BEKERJA. RASIO ARUS PICK UP DENGAN DROP OFF I I pick up I reset I beban t t gangguan

RELAI ARUS LEBIH PENGUJIAN INDIVIDUAL RANGKAIAN PENGUJIAN TIMER START
21 TIMER 22 29 23 30 START STOP 24 25 26 220 Vac 27 13 R 28 Vdc 14 A 220 Vac SLIDE TRAFO ISOLASI RANGKAIAN PENGUJIAN

PORTABLE TEST SET RELAY TIPE TPR 22 CV
VOLTMETER CT SEC C2 C1 C0 P1 P2 T1 T2 1 2 MAKE BREAK OFF TIME LAMP A SELECTOR POWER ON FAULT B A TPR 22 CV OCR UCR OVR UVR OTHER RELAY TEST CONDITION MIN MAX 1 A 5 A 10 A 75 V 300V 150V B SELECTOR V EXT INT PORTABLE TEST SET RELAY TIPE TPR 22 CV

- + TPR 22 CV MCGG 82 OCR / GFR YANG DIUJI V
VOLTMETER CT SEC C2 C1 C0 P1 P2 T1 T2 1 2 MAKE BREAK OFF TIME LAMP A SELECTOR POWER ON FAULT B A TPR 22 CV OCR UCR OVR UVR OTHER RELAY TEST CONDITION MIN MAX 1 A 5 A 10 A 75 V 300V 150V B SELECTOR V EXT INT 16 21 22 23 24 25 26 27 28 13 14 + - C E/F MCGG 82 OCR / GFR YANG DIUJI 30 41 42 29 15 RANGKAIAN PENGUJIAN OCR/GFR DENGAN ALAT UJI TPR 22 CV

- PENGUJIAN RELAI OCR /GFR MCGG 82 + Vx t > t >> to>
HAND TERMINAL RELAI OCR / GFR MCGG 82 ALAT UJI XS92a ABB 21 13 + Vx - 22 14 23 29 24 t > 30 25 41 26 t >> 42 27 1 to> 28 2 15 to >> 16 RANGKAIAN PENGUJIAN RELAI OCR / GFR TIPE MCGG 82 IBA DOC 2003

DIAGRAM KONTROL DC PROTEKSI OCR/GFR (+) KONTAK OCR/GFR (+) RELAI BANTU
(-) TRIP PMT (+) RE 2 RELAI BANTU RE 3 ALARM (-)

DIAGRAM SIGNALISASI (+) KONTAK RELAI RESET TEST LAMP RELAI BANTU RE
LAMPU SIGNAL

x SINGLE LINE DIAGRAM FEEDER SCHEMATIC TYPE C2 A P2 V x5 fu1-3 x4 x3
LEGEN F1 F2 F3 PL1-3 P2 P31-2 S6 X3-X4 X5 HL1-3 Over Current & Earth Fault Relay Grounding Phase Detecting Relay Auto Recloser Relay Ammeter double scale 0 – 200/400/1A KV meter 20KV / 100V MWHmeter In - Out Selector Switch Volt 4 Position Current Test Blick Potential Test Block Neon Voltage Indicator SYMBOL 20KV/V3 100V/V3 Q2 125VA,CL 1,0 S6 HL1-3 T5 x5 T5 fu1-3 0,3A F1 F2 MCGG52 50 / 51 50G/51G MCGG22 50G/51G 200 – 400/ 1A,30VA,10P20 T1-3 TO METERING REMOTE CONTROL PANEL x4 x3 MWH MWH T1-3 A IN OUT 200 – 400/ 1A,15VA,0,5 P3-1 P3-2 PL1-3 F3 MVTR51 79 x Q1 630A SINGLE LINE DIAGRAM FEEDER SCHEMATIC TYPE C2 3PH,20KV,2500A,50Hz,25KA,3Sec Grounding Neutral Bar 2000a

POWER CIRCUIT PROTECTION FEEDER SCHEMATIC
L1 L2 L3 TLB 200 – 400 / 1A 30VA,10P20 X4 XB3 F1 21 22 F2 P1 2S1 27 2S2 2S3 2 2 2 MCGG52 MCGG22 P1 2S1 T1 2S2 3 03 3 28 2S3 25 26 Io > P1 2S1 T2 2S2 1 2 2S3 4 04 4 27 28 5 T3 7 1 01 1 6 I > Io >> TERMINAL 30 29 15 16 34 35 9 8 33 10 I >> 13 14 42 41 38 36 +T 37 13 110VDC 14 -T Io > 1 2 POWER CIRCUIT PROTECTION FEEDER SCHEMATIC 5 7 6 Io >> 15 16 9 8 10

CIRCUIT BREAKER CONTROL FEEDER SCHEMATIC +C +T M 2 4 4 2 1 3 1 3 38 8
LOCAL REMOTE M 2 4 4 2 S8 1 3 1 3 38 8 34 5 8 5 F1 F1 F1 F1 F2 F2 CB CLOSE OPEN 4 4 6 36 9 35 7 9 7 S1 7/4 3 2 3 5 S3 K4 15/8 S1 7/4 1 FROM RCP PANEL FROM BUCHOLZ TRIPPING ORDER FACILITY OPEN K3 15/6 CLOSE CIRCUIT BREAKER CONTROL FEEDER SCHEMATIC X 2 4 6 YL 1 3 M 5 Q1 YB KN OPEN N CLOSE -T - C

RANGKAIAN PENGUJIAN FUNGSI L1 L2 L3 Io > I > Io >>
TLB 200 – 400 / 1A 30VA,10P20 XB3 X4 F1 21 22 F2 P1 2S1 27 2S2 2S3 2 02 2 MCGG52 MCGG22 P1 2S1 T1 2S2 28 2S3 3 03 3 25 26 Io > P1 2S1 T2 2S2 1 2 2S3 4 04 4 27 28 5 T3 7 1 01 1 6 I > Io >> TERMINAL 30 29 15 16 34 35 9 8 33 10 I >> 13 14 TEST SET INJEKSI SEKUNDER 42 41 38 36 +T 37 13 110VDC 14 -T Io > 1 2 RANGKAIAN PENGUJIAN FUNGSI 5 7 6 Io >> 15 16 9 8 10 IBA 2006

SETTING OCR GANGGUAN FASA – FASA [ TUNDA WAKTU

KOORDINASI OCR # DEFINITE TIME A B C t 1,3 det 0,8 det 0,3 det I

KOORDINASI OCR # INVERSE TIME A B C t I
SETING WAKTU DENGAN PEMILIHAN TD / TMS TD = TIME DIAL TMA = TIME MULTIPLE SETTING A B C t TMS B TMS C TMS A I

SETTING ELEMEN INSTANTANEOUS
DIMAKSUDKAN UNTUK GANGGUAN 3 FASA ,TETAPI HARUS MEMPERHATIKAN ARUS KETAHANAN KABEL . SETTING INSTANT

KOORDINASI OCR # INSTANTANEOUS A B C

KOORDINASI DARI RELAI KOMBINASI TUNDA WAKTU DENGAN INSTANT /
C t t A t B t C t INST t INST I t TMS B TMS C TMS A t INST t INST I

SETTING GFR [RELAI GANGGUAN TANAH ] PERLU DIPERHATIKAN ;
SISTEM PENTANAHAN TITIK NETRAL BESARNYA ARUS HUBUNG SINGKAT SATU FASA KE TANAH . ARUS KETIDAKSEIMBANGAN BEBAN ARUS KAPASITANSI JARINGAN .

SISTEM PENTANAHAN DENGAN TAHANAN RENDAH
PADA SKTM SPINDEL BATAS MINIMUM ADALAH RELAI PADA SALURAN YANG SEHAT TIDAK BOLEH BEKERJA OLEH ARUS KAPASITANSI # PADA SUTM SAMA SEPERTI DI SKTM

@ SISTEM PENTANAHAN LANGSUNG [ SOLID ]
KARENA ARUS GANGGUAN BESAR , KRITERIA SETTINGNYA SEPERTI PADA RELAI PENGAMAN ANTAR FASA . TETAPI BATAS MINIMUMNYA LEBIH KECIL DARI ARUS BEBAN , TETAPI LEBIH BESAR DARI ARUS KETIDAKSEIMBANGAN BEBAN .

@ SISTEM MENGAMBANG RELAI TEGANGAN NOL RELAI INI TIDAK BOLEH BEKERJA BILA TERJADI PERGESERAN TEGANGAN NOMINAL RELAI GANGGUAN TANAH BERARAH [ DIRECTONAL GFR ] @ SISTEM PENTANAHAN DENGAN TAHANAN TINGGI RELAI YANG DIGUNAKAN ADALAH DGFR . RELAI OCR SEBAGAI GFR TIDAK DAPAT DIPAKAI . KARENA ARUS GANGGUAN SATU FASA KETANAH LEBIH KECIL DARI ARUS KAPASITANSI .

PORTABLE TEST SET RELAY TIPE TPR 22 CV
VOLTMETER CT SEC C2 C1 C0 P1 P2 T1 T2 1 2 MAKE BREAK OFF TIME LAMP A SELECTOR POWER ON FAULT B A TPR 22 CV OCR UCR OVR UVR OTHER RELAY TEST CONDITION MIN MAX 1 A 5 A 10 A 75 V 300V 150V B SELECTOR V EXT INT PORTABLE TEST SET RELAY TIPE TPR 22 CV

- + TPR 22 CV MCGG 82 OCR / GFR YANG DIUJI V A A
21 13 + A - 22 14 23 B 29 1 2 T1 T2 P1 P2 C2 C1 C0 CT SEC VOLTMETER 220 V 24 30 MAKE TIME ON ON EXT 25 41 POWER C OFF ON 26 BREAK LAMP OFF FAULT 42 OFF INT OFF TPR 22 CV A SELECTOR 27 1 E/F 28 2 V A A 15 16 OVR UVR 75 V OCR UCR OTHER RELAY 150V 10 A MCGG 82 300V B 5 A B A OFF 1 A B SELECTOR MIN MAX MIN MAX TEST CONDITION OCR / GFR YANG DIUJI RANGKAIAN PENGUJIAN OCR/GFR DENGAN ALAT UJI TPR 22 CV

- PENGUJIAN RELAI OCR /GFR MCGG 82 + Vx t > t >> to>
HAND TERMINAL RELAI OCR / GFR MCGG 82 ALAT UJI XS92a ABB 21 13 + Vx - 22 14 23 29 24 t > 30 25 41 26 t >> 42 27 1 to> 28 2 15 to >> 16 RANGKAIAN PENGUJIAN RELAI OCR / GFR TIPE MCGG 82 IBA DOC 2003

PROSEDUR PENGUJIAN PARAMETER FR = 50 DFR= 0 DF = 0
FC = SESUAI JENIS GANGGUAN SQ = PU / DROP A = SQ = 2 IRA = A = 0 TO = AUTO TL = SQ = 1F0 TF = > t set A = 1 IN1 = 1 IN2 = 0 OU1= 0/1 OU2= 0 TI = 2 TT = 0 MOD= UI MT = 1 OP = 0 UI U = 57 V I = A PHI= 90 DU = 0 DI = 0,01 DPH=0 LUH = 220 LUL = 0 LIH = 20A LIL = 0 LPI =359 LPO = 0 UJI PU / DROP OFF START / - Sambungan ke kontak dilepas Uji waktu kerja [ sambungan ke kontak dipakai] START + 2X ENTER

FC = CODE GANGGUAN 111 = R KE E 112 = S KE E 113 = T KE E 121 = GANGGUAN R S 122 = GANGGUAN ST = GANGGUAN TR

ABB SPAJ 140 C 1 2 I>/In 80. . . 265 V dc/ac t> [s] 3
L1 L2 L3 Io IRF 1 SPAJ 140 C 2 I>/In V dc/ac V dc t> [s] k 3 8 RESET STEP I>>/In t>> [s] k REGISTER OPER. IND Io>/In to> [s] ko 1. IL1/In 2. IL2/In 3. IL3/In 4. Imax 5. t(I>)[%] 6. t(I>>) [%] 7. Io/In 8. t(I0>) [%] 9. t(Io>>)[%] 1. I> start 2. I> trip 3. I>> start 4. I>> trip 5. Io> start 6. Io> trip 7. Io>> start 8. Io>> trip 9. CBF Io>>/In to>> [s] ko 4 SGF PROGRAM SGR TRIP SGB 5 6 7

1. Lampu indikator Phase yang terganggu .
KETERANGAN GAMBAR : 1. Lampu indikator Phase yang terganggu . L1 menyala artinya phase R terganggu L2 menyala artinya phase S terganggu L3 menyala artinya phase T terganggu Io menyala artinya ada gangguan tanah. 2. Display Monitor : untuk indikator besarnya setting arus ; waktu dan indikator kerja . * Display Indikator besarnya arus sekunder ( I> , I>> , Io> , Io>> ) serta setting waktu ( t> / k> , t>> / k>> , to> / ko > , to>> / ko >> ) Untuk melihat setting tekan tombol (3) akan Muncul indikator besarnya setting. Display indikator kerja, bila indikator muncul angka sbb : I> start ( OCR ) I> trip ( OCR ) I>> start OCR Moment / Instant ) I>> trip ( OCR Moment / Instant ) Io> start ( GFR ) Io> trip ( GFR ) Io>> start ( GFR Moment / Instant ) Io>> trip ( GFR Moment / Instant )

3. Tombol Reset / Step a. berfungsi sebagai reset indikator kerja relai. b. berfungsi sebagai perubah step setting arus dan waktu bila difungsikan. 4. Tombol Program berfungsi untuk memprogram setting arus dan waktu sesuai setting yang diinginkan. 5. Lampu indikator trip ( warna merah ) Bila relai merasakan arus gangguan sampai t set ( setting waktu relai ) tercapai. Maka lampu indikator 5) akan menyala. 6. Lampu indikator setting arus dan waktu yang diinginkan. 7. Keterangan dari Display indikator kerja relai 2). 8. Lampu indikator untuk menunjukan bahwa tegangan dc di relai telah tersedia.

Internal diagram relai OCR / GFR SPAJ 140 C
UI 3I> Io> Io>> AC Setting Reset 5A 1A U1/SGR3/1 U1/SGR3/2 U1/SGR3/3 U1/SGR3/4 U1/SGR3/5 U1/SGR3/6 U1/SGR3/7 U1/SGR3/8 U1/SGR1/1 U1/SGR1/3 U1/SGR1/5 U1/SGR1/7 U1/SGR2/1 U1/SGR2/3 U1/SGR2/5 U1/SGR2/7 U1/SGR2/2 U1/SGR2/4 U1/SGR2/6 U1/SGR2/8 SGB6 SGB7 U1/SGR1/2 U1/SGR1/4 U1/SGR1/6 U1/SGR1/8 U1/SGB1 U1/SGB2 U1/SGB3 U1/SGB4 U1/SGB5 U1/SGB8 U2 U3 1 2 3 6 4 5 25 7 8 9 26 27 U1/SGF4 0,1…1s T9 T1 T3 T5 T7 T8 T6 T4 T2 TRIP SS3 TS2 TS1 SS1 SS2 A B C D E F 66 65 + Rx Tx 69 68 81 80 78 77 75 74 71 70 72 62 61 10 11 IRF START 2 START 1 SIGNAL 1 SIGNAL 2 r s t n Io Uaux 63 Internal diagram relai OCR / GFR SPAJ 140 C

CONTROL SIGNAL ANTAR MODUL SPAJ 140 C
SGR1/8 SGR2/8 SGR2/7 SGR3/8 SGR1/7 SGR3/7 SGR1/6 SGR2/6 SGR2/5 SGR3/6 SGR1/5 SGR3/5 SGB3 SGB4 SGB6 SGB5 > Io >> Io > to> ko to>> SGB1 SGB2 IL3 IL1 IL2 BS Io I >> t>> I > t> k SGR3/4 SGR1/4 SGR2/4 SGR2/3 SGR1/3 SGR3/3 SGR1/2 SGR2/2 SGR2/1 SGR3/2 SGR1/1 SGR3/1 1 SGB/7 RESET PROGRAM SGB/6 SGF1/4 SGF2/8 0,1..1S AR1 AR2 AR3 TS1 SS2 SS3 SS1 TS2 IRF F E D START 1 START 2 SIGNAL 1 C SIGNAL 2 B TRIP A SPTU R1 REDUCED BLOCK DIAGRAM SPCJ 4D 29 REMOTE SETTING RELAY RESET TRIP CONTROL SIGNAL ANTAR MODUL SPAJ 140 C

1. Setelah relai disambung ke Aux. supply dc , melalui terminal
CEK MULA OCR/GFR SPAJ 140 C 1. Setelah relai disambung ke Aux. supply dc , melalui terminal relai nomer 61 [+] dan 60 [-] , sesaat kemudian lampu indikator U aux. menyala dan display menyala per segmentnya, kemudian display akan padam . 2. Kemudian cek lampu indikator Trip, caranya sebagai berikut : # tekan tombol push botton STEP RESET sehingga display menunjuk seperti gambar di bawah ini . STEP RESET I>/In t> [s] k n x 1s I>>/In t>> [s] k # kemudian tekan push botton PROGRAM kira kira 5 detik sampai display menunjuk seperti gambar dibawah ini. Io>/In to> [s] ko Io>>/In to>> [s] ko PROGRAM SGF 5s SGR TRIP SGB

kira kira 1 detik sampai display menunjuk seperti gambar dibawah ini
# kemudian tekan tombol push botton PROGRAM kira kira 1 detik sampai display menunjuk seperti gambar dibawah ini ( lampu indikator t>, t>>, to>, to>> menyala ) I>/In t> [s] k RESET STEP I>>/In t>> [s] k Io>/In to> [s] ko PROGRAM Io>>/In 1s to>> [s] ko SGF PROGRAM SGR TRIP # kemudian tekan tombol push botton STEP/RESET dan PROGRAM secara bersamaan ,maka lampu indikator TRIP akan menyala dan display menunujuk seperti dibawah ini ( berarti oke ) SGB I>/In t> [s] k RESET STEP I>>/In RESET STEP t>> [s] k Io>/In to> [s] ko Io>>/In to>> [s] ko PROGRAM SGF 1s PROGRAM SGR TRIP SGB

3. Dengan kondisi display seperti dibawah, kemudian tekan
tombol push botton RESET / STEP maka lampu indikator IRF akan menyala . IRF RESET STEP I>/In 1s t> [s] k RESET STEP I>>/In t>> [s] k Io>/In to> [s] ko Io>>/In to>> [s] ko SGF PROGRAM SGR TRIP SGB

SGF (Switch Group for Function) SGF terbagi atas dua bagian yaitu :
PROGRAM SWITCH GROUP SGF, SGB, SGR SGF (Switch Group for Function) SGF terbagi atas dua bagian yaitu : 1.1. SGF 1 1.2. SGF 2 1.1. SGF1 terbagi atas 8 bagian sebagai berikut : SGF1/1 SGF1/2 SGF1/3 SGF1/1 SGF1/2 SGF1/3 Mode operasi Karakteristik definite time ,05 … s IDMT Extremely inverse idem Very inverse idem Normal inverse idem Long time inverse idem karakteristik R I idem karakteristik RX1DG tidak digunakan Dipakai untuk menentukan / memilih karakteristik kerja dari I > yang diinginkan

SGF1/4 dipakai sebagai Breaker Faillure Protection (CBF)
atau tidak SGF1/ dipakai untuk melipat gandaka nilai setting I >> secara otomatis bila dipasang pada level inrush current. SGF1/6 SGF1/7 SGF1/8 Dipakai untuk memilih karakteristik kerja dari Io> yang diinginkan. SGF1/1 SGF1/2 SGF1/3 Mode operasi Karakteristik definite time ,05 … s IDMT Extremely inverse idem Very inverse idem Normal inverse idem Long time inverse idem karakteristik R I idem karakteristik RX1DG tidak digunakan

1.2. SGF2 terbagi atas 8 bagian sebagai berikut :
SGF 2/5 dipakai untuk mengaktipkan atau tidak arus Moment ( I>> ) SGF2/6 dipakai untuk mengaktipkan atau tidak arus Moment gangguan tanah ( Io>> ) SGF2/7 dipakai untuk mengaktipkan atau tidak recloser (bila diperlukan , input dari signal starting I> / I>> ). SGF2/8 dipakai untuk mengaktipkan atau tidak recloser ( bila diperlukan, input dari signal starting Io> / Io>> ). Dipakai untuk mereset secara manual atau otomati Dari indikator starting I > / I>> / Io> /Io>>.

2. SGB ( Switch Group for Blocking )
SGB1/5 saklar ini memungkinkan merubah dari setting utama ke setting ke dua dan sebaliknya tanpa komunikasi, menggunakan input signal external control BS SGB1/6 untuk memilih sebuah penghalang untuk signal tripping TS2 untuk gangguan phase. SGB1/ untuk memilih sebuah penghalang untuk signal tripping TS2 untuk gangguan tanah. SGB1/ Resetting secara remote ( jarak jauh ) sebuah penghalang output relai. Dipilih bila external control signal BS digunakan untuk memblokir satu atau lebih dari tingkatan arus dari modul.

3. SGR (Switch Group for Relay Configuration)
SGR ini terbagi ke dalam 3 bagian yaitu : 3.1. SGR1 3.2. SGR2 (stage – 2 ) 3,3. SGR3 3.1. SGR1 Saklar ini digunakan untuk memilih tingkatan proteksi yang dibawa ke output signal starting SS1 dan output signal tripping TS2 . SGR1 ini terbagi atas : SGR1/1 untuk signal starting tingkat I> disambung ke SS1 ( terminal relai nomer 77 – 78 ). SGR1/2 untuk signal tripping tingkat I> disambung ke TS2 ( terminal relai nomer 65 – 66 ). SGR1/3 untuk signal atarting tingkat I>> disambung ke SS1 ( terminal 77 – 78 ). SGR1/4 untuk signal tripping tingkat I>> disambung ke TS2 ( terminal 65 – 66 ). SGR1/5 untuk signal starting tingkat Io> disambung ke SS1 ( terminal SGR1/6 untuk signal tripping tingkat Io> disambung ke TS2 ( terminal SGR1/7 untuk signal starting tingkat Io>> disambung ke SS1 ( terminal SGR 1/8 untuk signal tripping tingkat Io>> disambung ke TS2 ( terminal

3.2. SGR2 Saklar ini dipakai untuk konfigurasi signal tripping tingkat
proteksi yang berbeda . Mempunyai dua output SS2 dan SS3 yang mana signal dapat disambung. SGR2 ini terbagi atas : SGR2/1 untuk signal starting tingkat I> disambung ke SS2 ( terminal relai no 80 – 81 ) SGR2/2 untuk signal tripping tingkat I> disambung ke SS3 ( terminal relai no 68 – 69 ) SGR2/3 untuk signal starting tingkat I>> disambung ke SS2 ( idem SGR2/1 ) SGR2/4 untuk signal tripping tingkat I>> disambung ke SS3 ( idem SGR 2/2 ) SGR2/5 untuk signal starting tingkat Io> disambung ke SS2 ( idem SGR 2/1 ) SGR 2/6 untuk signal tripping tingkat Io> disambung ke SS3 SGR2/7 untuk signal starting tingkat Io>>disambung ke SS2 SGR2/8 untuk signal tripping tingkat Io>> disambung ke SS3

3.3. SGR 3. Saklar ini dipakai untuk konfigurasi signal starting dan tripping
untuk output starting atau auxiliary tripping TS1 Catatan : Jika proteksi CBF (Circuit Breaker Failure ) dipilih pada SGF 1/4 ,ini juga menggunakan output TS1. SGR3 terbagi atas { SGR3/ untuk signal starting tingkat I> disambung ke TS1 ( terminal relai nomer 74 – 75 ) SGR3/ untuk signal starting tingkat I> disambung ke TS1 ( idem SGR3/1 ) SGR3/ untuk signal starting tingkat I>> disambung ke TS1 SGR3/ untuk signal starting tingkat I>> disambung ke TS1 ( idem SGR 3/1 ) SGR3/ untuk signal starting tingkat Io> disambung ke TS1 SGR3/ untuk signal starting tingkat Io> disambung ke TS1 SGR3/ untuk signal starting tingkat Io>> disambung ke TS1 SGR3/ untuk signal starting tingkat Io>> disambung ke TS1 ( idem SGR 3/1 ).

1 n x 1 s 1 s CARA SETTING ( PEMROGRAMAN )
Setelah CEK MULA item 1. dilakukan ,kemudian lakukan Penyetelan pada : 1. SGF 1 (Switch Group of Function ) SGF1/1 SGF1/2 SGF1/3 Untuk menentukan karakteristik waktu ,misal kita pilih adalah Definite time maka : SGF1/1 diset = 0 SGF1/2 diset = 0 SGF1/3 diset = 0 CARANYA : a) Tekan push botton STEP-RESET sampai lampu Led Indikator SGF menyala dan display menunjuk seperti dibawah ini : b) Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini ; RESET STEP n x 1 s PROGRAM 1 1 s

c) Kemudian tekan push botton PROGRAM kira kira 5 detik sehingga
display menunjuk seperti gambar dibawah Kemudian tekan push botton PROGRAM 1 kali sehingga display menunjuk seperti gambar dibawah ini Kemudian tekan push botton PROGRAM kira kira 1detik,sehingga display menunjuk seperti dbawah ini PROGRAM 1 5 s SGF 1 / 1 = 0 PROGRAM 1 1 1x SGF 1 / 2 = 0 PROGRAM 1 2 1s

Kemudian tekan push botton PROGRAM kira kira 1 detik,sehingga display menunjuk seperti dibawah ini
Selanjutnya lakukan seperti program diatas untuk program selanjutnya : SGF1/4 = Bila dioperasikan sebagai back up ( Breaker Failure protection = CBF) SGF 1/4 = Bila tidak dioperasikan sebagai back up (CBF) SGF 1/5 = Bila dipakai sebagai proteksi terhadap inrush SGF 1/5 = bila tidak dipakai SGF 1/6 = 0 SGF 1/7 = 0 SGF 1/8 = 0 Catatan : Bila menghendaki perubahan misalnya dari posisi SGF1/4=0 menjadi SGF1/4=1 SGF 1 / 3 = 0 PROGRAM 1 3 1s

Catatan : Bila menghendaki perubahan misalnya dari posisi SGF1/4=0 menjadi SGF1/4=1
Caranya : Tekan push botton STEP/RESET 1 kali sehingga perubahan display menjadi seperti dibawah ini STEP RESET 4 1 1 4 1 1X Setelah pemrograman SGF1/1 s/d SGF1/8 selesai, maka dilakukan penyimpanan . Dengan posisi SGF1/1 s/d SGF1/8 semuanya = 0 maka cara penyimpanannya adalah sbb: Tekan push botton PROGRAM kira kira 5 detik, sehingga display menunjuk seperti gambar dibawah PROGRAM Merupakan total ( checksum dari SGF ) 5s 1 tekan push botton STEP/RESET dan PROGRAM secara bersamaan sehingga display menunjuk seperti gambar dibawah STEP/RESET Selanjutnya display menunjuk 1 - - - 1 PROGRAM Artinya semua data Yelah disimpan IBA DOK

2. SGF2 Untuk pemrograman SGF2 disetting sebagai berikut : - SGF2/1 s/d SGF2/4 diset = 1 ( reset secara manual ) - SGF2/ diset = 0 ( I >> dioperasikan ) - SGF2/ diset = 0 ( Io >> dioperasikan ) - SGF2/ diset = 0 ( I >> tidak dipakai recloser ) - SGF2/ diset = 0 ( Io >> tidak dipakai recloser ) Checksum = 15 3. SGB ( Switch Group for Blocking ) Setelah pemrograman SGF selesai, kemudian tekan push botton STEP/RESET sehingga lampu LED SGF padam dan lampu LED SGB menyala/ Kemudian lakukan pemrograman / setting untuk SGB , caranya sama seperti pemrograman pada SGF. Dalam hal ini program SGB 1/1 s/d SGB1/8 di set = 0 Checksum = 0 ( baca buku petunjuk / instruction manual ) 4. SGR ( Switch Group of Relay Configuration ) Setelah pemrogram SGB selesai , kemudian kita tekan push botton STEP/RESET sehingga lampu LED SGB padam dan lampu LED SGR menyala.

4. SGR ( Switch Group of Relay Configuration )
Setelah pemrogram SGB selesai , kemudian kita tekan push botton STEP/RESET sehingga lampu LED SGB padam dan lampu LED SGR menyala. Kemudian lakukan pemrograman ( setting ) untuk SGR caranya sama seperti pemrograman pada SGF. Dalam hal ini program SGR diset sebagai berikut : - SGR 1/1 s/d SGR 1/8 di set = checksum = 255 - SGR 2/1 s/d SGR 2/8 di set = checksum = 0 - SGR 3/1 s/d SGR 3/8 di set = checksum = 0

0. 8 1 0. 8 5. CARA PEMROGRAMAN ( SETTING )
I > / I >> / Io > / Io >> / t > / t >> / to > / to >> 5.1. Setting I > : misalnya Iset = 1,05 x In Caranya sebagai berikut : a. Tekan push botton STEP/RESET kira kira 5detik sehingga lampu Led I > menyala dan display menunjuk seperti dibawah ini . STEP/RESET 5s 0. 8 b. Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini . PROGRAM 1s 1 0. 8

c. Kemudian tekan push botton PROGRAM kira kira 5 detik sehingga display menunjuk seperti dibawah ini. PROGRAM 5s 1 0. 8 d. Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini. PROGRAM 1s 1 0. 8 e. Kemudian tekan push botton STEP/RESET 5 kali sehingga display menunjuk seperti dibawah ini. STEP/RESET 5x 1 0. 8 5

f. Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini. PROGRAM 1s 1 0. 8 5 g. Kemudian tekan push botton STEP/RESET kira kira 2 kali sehingga display menunjuk seperti dibawah ini. STEP/RESET 2x 1 0. 5 h. Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini. PROGRAM 1s 1 0. 5

i. Kemudian tekan push botton STEP/RESET kira kira 1 kali sehingga display menunjuk seperti dibawah ini. STEP/RESET 1x 1 1. 5 j. Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini. PROGRAM 1s 1 1. 5 k. Kemudian bila kita menghendaki perubahan titik desimal (memindahkan titik desimal), maka tekan push botton STEP/RESET sesuai keinginan kita.

l. Kemudian tekan push botton PROGRAM kira kira 1 detik sehingga display menunjuk seperti dibawah ini. PROGRAM 1s 1 1. 5 m. Kemudian tekan push botton PROGRAM dan STEP /RESET secara bersamaan, sehingga display menunjuk seperti dibawah ini. STEP/RESET Artinya semua data disimpan 1 - - - Selanjutnya display menunjuk PROGRAM 1 1. 5

Catatan : - Jika menghendaki untuk pemrograman ( setting ) STAGE 2 , Setelah melakukan langkah m) , kemudian tekan push botton PROGRAM kira kira 5 detik, sehingga display menunjuk seperti dibawah ini . PROGRAM 5s 1 1. 5 - Kemudian tekan push botton STEP/RESET kira kira 1 detik (untuk merubah angka stage ) sehingga display menunjuk seperti dibawah ini. STEP/REET 1s 2 1. 5 Setelah itu lakukan seperti langkah langkah (prosedur ) d) s/d m) 5.2. Setting I >> / t > / t >> / Io > / Io >> / to > / to >> lakukan pemrograman seperti cara Setting I > .

Presentasi serupa